In climates and applications where unusually high relative humidity exists, warm humid air contacting a cold motor will cause condensation that can lead to accelerated deterioration of motor parts. Condensation does not exist while the motor is running because the heat generated by the motor keeps the motor dry. However, when the motor is shut down, condensation starts to form; the longer the idle period, the more pronounced the rate of deterioration.
The most common method of combating this condensation problem is with the installation of small electric heating elements inside the motor. The normal heaters used in U.S. MOTORS® brand product are silicone rubber strip heaters which can be installed in the field on most standard motors by removing the brackets and wrapping the strip heaters around the winding end turns. In order to obtain the correct wattage the heaters are either connected in series or parallel and leads are brought out to the standard conduit box. A second separate conduit box can be provided when specified by the customer.
Trickle Voltage Heating
Another method of combating condensation is Single Phase Low Voltage Heating called "trickle heating." This method is especially adaptable to our method of insulation and can be added in the field without any changes to the motor. This system maintains 10 to 20 percent of the nameplate voltage in the motor winding when the motor is shut down. This low voltage results in a temperature rise of approximately 10ºC above ambient temperature. A 10ºC rise is normally adequate to prevent damaging condensation.
The trickle heating system applies voltage to two of the three motor leads. A single phase dry type, two winding transformer applies this voltage after the three phase power has been removed. Since the applied power is low voltage, single phase, the motor will not rotate with the trickle voltage applied.
To be effective the current should be approximately 25 to 35% of nameplate amps.
The dry type, two winding, transformer should have +5% and +10% voltage taps for final voltage adjustment. Refer to Technical Service for the required transformer secondary voltage and KVA rating recommendations, since this will vary with motor ratings.
The following are some of the advantages of this system over conventional space heaters:
Heating in Hazardous Locations
Transformer secondary voltage should be 10-20% nameplate. Amps will be 25-35% of nameplate. Transformer should have +5% and +10% primary voltage taps, refer to Technical Service for recommended transformer rating.
Refer to Electrical Code in your area, certain connections may not necessarily be in accordance with local electrical code.